Frequently Asked Questions
We have one set of 1 Transmitter and 1 IS Isolator. I approached this in 2 different ways. Option 1) transmitter + IS Isolator in Sensor Group 1. Option 2) Transmitter in Sensor Group 1 + IS Isolator in Sensor Group 2. The PFDavg were same between Option
Last Updated a year ago
Option 1 is correct since the devices are in series. Option 2 suggests that they are redundant and can both measure the same process value which is incorrect. This is why the results are different.